Use is confined to Engineers with more than 370 course hours of electronic engineering for theoretical studies. <p> ph +1(785) 841-3089 Email email@example.com
Thermostat signals and wiring
 Thermostat signals and color code
 Lack of standards makes this interesting.
While there isn't an official standard for thermostat circuit wiring colors, there is a general pattern. Your best bet is to see the manufacturer's documentation (both thermostat and HVAC).
 Wire colors
If you only have 4 wires - typically: (Red, Yellow, Green & Black), or (Blue, White & Blue stripe, Orange, White & Orange stripe, and possibly Green & Brown pairs as well.) coming out of the wall - that is probably phone or networking wire and it isn't good because it is too thin for the current. If there is a short it is possible it could cause a fire (Thermostat wires are usually #18 gauge.) These colors are not standard for thermostats.
If you need an inexpensive meter to work with thermostat wiring see M300
We also have meters that can display thermocouple temperature Process Control Meters
|Older systems and base signals on newer ones|
|C||Black||24 Vac Common||From one side of the 24Vac transformer (Think of this as 24Vac neutral|
|R or V||Red||24 Vac Power to be switched||From other side of the 24Vac transformer (Think of this as 24Vac L1)|
|Rh or 4||Red||24 Vac Heat call switch power||Same as R, but dedicated to the Heat call switch|
|Rc||Red||24 Vac Cooling call switch power||Same as R, but dedicated to the cooling call switch|
|G||Green||Fan||Fan switch on thermostat - is connected to R when Fan /Auto switch is in the fan position|
|W||White||Heating call||Is connected to R or Rh when themostat calls for heat. (Might be jumpered to Y on a heat pump. On others might be second stage heating|
|Y||Yellow||Cooling call|| Is connected to R or Rc when themostat calls for cooling. Also Cooling or 1st stage heating on a heat pump |
Most often connected to G when Fan switch is set to auto
|New signals - for heat pumps and staged systems|
|Y2||Blue or Orange||2nd stage Cooling|
|W2||Varies||Second Stage Heating||First stage Auxiliary heating on a heat Pump|
|Emergency heat relay on a heat pump. Active all the time when selected, usually not used.||Disable the heat pump and turn on first stage Aux heating|
|Reversing valve (relay switch energized to cool)||Energize to cool (changes from heat to cool on heat pumps)|
| Sometimes common side of transformer. Needed on some electronic thermostats or if you have indicator lamps
Reversing valve (relay switch energized to heat) in contrast to (O) above.
|Might be heating changeover from cooling or, on older stuff, the common of transformer. York and Trane sometimes use (B) as common.|
|X||Varies||SEE NOTES BELOW||Might be common but sometimes emergency heat relay|
|X2||Varies||Second stage heating or indicator lights on some thermostats||Might be emergency heat relay|
tan or gray
|Outdoor anticipator reset||Used on GE/Trane/American Standard and some Carrier Products.|
 Conventional thermostats
(Single stage heating and cooling using gas, electric or oil heat)
This is often referred to as a 1H/1C conventional thermostat
 Terminal designations
The usual terminals are:
- G – Fan, usually a green wire
- R – 24 VAC usually a red wire (Rc and Rh are discussed later)
- C – 24 VAC Common
- Y – Compressor, usually a yellow wire
- W – Heat, usually a white wire
The thermostat is a set of contacts where G, W and Y are connected to R based on the following rules.
If there is a call for cool, R is connected to Y (compressor). In air conditioning mode the thermostat controls the fan, so G (Fan) is also connected to R. For cooling, the furnace usually selects the high speed of the blower.
In conventional heating which is oil or gas, the furnace controls the fan, so only R is connected to W (heat). For electric heating, the thermostat controls the fan (G), thus in this case both G (Fan) and W (heat) are connected to R (24 VAC). For heating applications, a lower blower speed is used and the furnace selects it.
The furnace controls the fan because oil and gas heat is not instantaneous. In order to avoid a blast of cold air, the furnace controls the fan. It can do this with a simple delay or by temperature set by the limit switch in the plenum.
Humidification is a fan-only function; humidifiers may be controlled by the G (fan) terminal.
 Rc, Rh and R
Rc and Rh have been added to accommodate separate transformers for cooling and heating, respectively. Thus, for single transformer systems, Rc and Rh are jumpered together and assume the function of the R terminal. Some systems use R and Rc; so consider R to be Rh in this case. Rc is defined as R (cooling) and Rh is defined as R (heating). Often, both letters are in uppercase as in RC and RH.
 The Fan (G) terminal
The Fan (G) terminal is usually connected to Rc when Rc exists on the thermostat.
 The Common terminal
The common terminal has been a recent addition because early thermostats created the switches with the liquid metal mercury. Mercury is a hazardous material and must be disposed of properly. Electronic thermostats need power to operate and it would like both a hot and a common terminal to get power or both ends of the transformer secondary need to be available to the thermostat.
There is a technology called “power stealing” where unopened switches can power thermostat. The current available is limited by the resistance of the furnace relays.
Power can also be provided by a set of batteries. When the batteries die, you then have no air conditioning or heating.
 The Clock
Programmable thermostats require a way to know the time and it needs to know the time during power outages. A thermostat may contain a small lithium battery just as your laptop or PC does. The manufacturer usually doesn’t even tell you about them. “Remove/pull this paper” before use is a good indication that the thermostat contains an internal battery. The battery may be rechargeable or it can be implemented using a supercap or Super capacitor. These are very high value capacitors which can run the clock for maybe a day or so.
 Setpoints/programs/configuration parameters
Your setpoints in an electronic thermostat are not susceptible to being lost when the power fails because they are stored using a different technology. The technology is continually evolving, but the lifetime may be 10 years or more with say 15,000 write cycles.
 Anticipator/thermal lag
Old mercury thermostats used to pass a specific current through the bi-metallic spring to artificially raise the temperature, so the heat cuts off sooner and the building releases this stored heat into the environment. The spring tension provided the hysteresis so that say if the stat was set at 72, it would turn on for heat at 72 and it would turn off at say 73.
While not likely used on a home furnace - One of the most used methods of control is the PID algorithm. PID stands for Proportional Integral Derivative. The proportional term operates directly on the difference between the current value and the setpoint. This gets you close set point. The Integral terms operates on a running summation between setpoint and the current current value. This essentially ensures you get to the setpoint. The Derivative term operates on the rate of change of the difference between the set point and the current value. This allows a final tuning of the algorithm so to remove over/undershoot of the set point for maximum comfort.
Thermostats can automatically find the values of P, I and D, but it may take it some time. This is called auto-tuning. By using auto-tune algorithms the thermostat can have a better chance of being at say 68 deg at 8:00 when you program that time and temperature.
 Temperature measurement (heat pump and conventional)
Thermistors are a common way to measure temperature. These are temperature dependent resistors with a non-linear known behavior and they are cheap and not polarity sensitive. They may be used as external temperature sensors so that it can measure the outside temperature or control the temperature at a different place than where the thermostat is located.
Solid state sensors could also be used and would most likely be used inside the thermostat.
The outside temperature should be known to a heat pump control so it can measure what’s called a “balance point”. The balance point is when the heat pump output is just equal to the heat loss required to heat the home. At the balance point the heat pump will run all the time just to break even. If the outside temperature gets below this balance point, then supplementary electric or other heat is required to maintain the inside temperature. There is also an outside cut-off temperature where below that temperature the heat pump is no longer economical and only the supplementary heat should be used. Dual fuel systems cannot allow the heat pump and a gas or oil furnace to operate at the same time.
Controls - Fan (Auto/On)
Controls Mode – Auto/Heat/Off/Cool
Controls - Setpoint